The SmartServer IoT Starter Kit includes an Advantech ADAM-4150 DIO module. This module includes LEDs that indicate the state of the module’s digital outputs. A pair of switches to the right of the module are connected to inputs DI-0 and DI-1 as shown in the figure below. Two of the wires loop back connecting outputs DO-0 to DI-2, and DO-1 to DI-3.
Get started setting up the Modbus RTU channel following the steps in the section below: Getting Started with Modbus RTU Channel Setup.
Enter the following command: cd /var/apollo/data/apps/adam-setup
Enter the following command: unzip adam-setup.zip
Enter the following command: rm adam-setup.zip
Power down the ADAM-4150 module by unplugging the bottom power supply connector.
Move the configuration switch from the Normal to Init position.
Power up the ADAM-4150 module by plugging in the bottom power supply connector. With the following step, the ADAM-4150 module to setup to use Modbus address 01 and to communicate at 19200 Baud, no parity, and one stop bit.
Enter the following command: node adamConfig.js 01 7
This command configures the ADAM-4150 module to use a 19200 Baud serial Modbus at address 01.
You should see a result similar to the following:
Power down the ADAM-4150 module by unplugging the bottom power supply connector.
Move the configuration switch from the Init to Normal position. If you neglect to move the switch to the Normal position, the module will not use the Modbus settings that were just programmed.
Power up the ADAM-4150 module by plugging in the bottom power supply connector.
Note: It is only necessary to set the configuration switch as described in this procedure one time for the ADAM-4150 module. If you are not sure about the programmed state of the ADAM-4150 module, move the switch to the Init position and perform steps #9-13 above.
Continue setting up the Modbus RTU channel following the steps in the section below: Setting the RS-485 Configuration UI.
Configure your RS-485-1 settings to match those shown in the figure below. When you configured the ADAM-4150 module at Modbus address 01, you also set the serial bit rate it would use to communicate. The above instructions set the baud rate to 19200. The module's serial frame does not use parity and looks for only 1 stop bit.
Continue setting up the Modbus RTU channel following the steps in the section below: Creating a Modbus Device.
Creating a Modbus Device
Now that the ADAM-4150 module is prepared to be accessed as a Modbus RTU device, with Modbus address of 01 and a 19200 Baud serial connection, the device can be added to the SmartServer IoT. To create a Modbus device, perform the following steps:
Open the SmartServer CMS by clicking the CMS tab on the Configuration UI, or by entering the URLhttps://[SmartServer IP address]/cms/#/login.
Click the Import / Export button () on the main CMS dashboard.
For SmartServer 3.6 and prior
For SmartServer 3.6 and prior, you can also use the Import Device Types button () on the Device Types widget to load the DTP file.
Import / Export button () on the main CMS dashboard
Notification messages (similar to the one shown below) will appear indicating that device types are being uploaded and the CPU usage on the main CMS page will show increased activity.
When the device types file has finished loading, click CANCEL to close the Import / Export dialog.
Go to the Devices widget, EDGE DEVICES tab, which will be used to add a Modbus device to the system.
Click the Create button () to add the Modbus device, setting the following fields as shown in the figure below:
Integration method: Manual assignment
Device type: ADAM-4150
Click SAVE. The DIO device is added to the Devices widget.
Click the Action button () for the DIO device and select the Provision action.
Within a few seconds, the DIO device fill should change from blue to green indicating that the device has be successfully provisioned. If the provision fails, confirm that the Modbus channel on RS-485-1 is set for 19200, no parity, and one stop bit as described in the previous section Setting the RS-485 Configuration UI.
Warning:With SmartServer IoT release 2.8, the Modbus engine is locked in to communicate to the device with the channel parameters already configured at device creation. If the Modbus channel parameters are changed, you will need to remove the Modbus device and recreate it.
Begin using the DIO module following the steps in the section below: Interacting with the DIO Module.
Interacting with the DIO Module
Using the Datapoint Properties Widget
The ADAM-4150v20.dtp package defines the interface to access the digital input and output of the ADAM-4150 device using Modbus RTU and the RS-485-1 channel. This package includes a .dla file that provides Modbus driver instructions for monitoring the data and presenting the data events to the rest of the system. The Adam-4150V20.dla.csv file is contained ADAM-4150v20.dtp archive that was imported in the process of Creating Modbus a Devices.
Follow the steps below to take a closer look at how this works.
Go to the Datapoint Properties widget. Click the Expand button ( ) for a better view of this widget. To reduce the scope of data that appears on the Datapoints widget, set the filter to narrow down the display to Modbus driver.
Notice that the Monitored attribute is set to On as shown below.
To edit datapoint properties for Datapoint DI_0, click the Action button () and select the Edit action.
The Edit Datapoint Properties view appears.
Click the MONITORING AND LOGGING CONFIGURATION tab. As shown in the figure below, the Monitored Yes option should be enabled. Since the Modbus driver can only poll datapoints, for the values to be monitored continuously, the Polled (Monitoring Method) option should also be enabled. Poll Interval (Seconds) is set to 2 and Publish Minimum Delta Value is set to On Any Change.
These settings are important because the event traffic that would be created with 14 datapoints being polled every 2 seconds would needlessly consume CPU cycles. Therefore, if you are not using some of the inputs or outputs in your system, you should disable monitoring for the associated datapoints. (This optimization is not required for a small demonstration panel.)
Exit fullscreen mode for the Datapoint Properties widget by clicking the Collapse button ().
Using the Datapoints Widget
Notice in the figure below that DI_0 is connected to the top switch and DI_1 is connected to the middle switch. The outputs DO_0 and DO_1 connect to inputs DI_2 and DI_3 respectively.
In the steps that follow, you will use the Datapoints widget to monitor and interact with these points. Follow the steps below to take a closer look at how this works.
Go to the Datapoints widget. Click the Expand button ( ) for a better view of this widget. To reduce the scope of data that appears on the Datapoints widget, set the filter to narrow down the display to Modbus driver.
Since monitoring is enabled for the DIO module points, polling done by the Datapoints widget is redundant and not necessary. Therefore, before getting started with the Datapoints widget, you will need to change the Poll Interval (Seconds) on the Datapoint Properties widget from 2s to 0s. With Poll Interval (Seconds) set to 0s on the Datapoint Properties widget, the Refresh button () on the Datapoints widget (shown in the figure below) can be used to force a get of the current value.
Select the checkmark next to each of the following six datapoints: DI_0, DI_1, DI_2, DI_3, DO_0, and DO_1 (the checkmark changes from blue to yellow). Use the scroll bar as needed to select all of the desired devices.
Click the Action button () on the Datapoints widget and select the Show Selected Datapoints action.
The Datapoints display is updated with only the six selected datapoints.
The action of the switches on the Starter Kit, and the modification of DO_0 and DO_1 values in the Datapoints widget, will be reflected within the 2s poll interval that is defined in the Adam-4150V20.dla.csv file. This file iscontained in the ADAM-4150v20.dtp archive that was imported in the process of Creating Modbus a Device.
Exit fullscreen mode for the Datapoints widget by clicking the Collapse button ().
You have succeeded integrating a simple Modbus RTU device with the SmartServer IoT. Success requires device setup and serial frame compatibility. As with all RS-485 based devices, it is important to pay attention to the communication wire polarity, and the inclusion of the common ground. Go to Creating Devices to set up other devices.